Cooperative: current membership of 917. 1,200 customers are supplied with a total of 58,3 Mio. kWh of district heating. An additional 8,3 Mio. kWh of renewable electrical power is produced each year and supplied to another 3,500 households.
Heating facility built in: 1995, Boiler I and II: Boiler output: 2 x 4,000 kW
Electrical power facility built in: 2003; operation resumed (after fire) in 2012
Boiler III: Boiler output: 10,000 kW; built in: 2003 and 2012, Electrical power plant: built in 2003, ORC turbine 1,500 kWel (not damaged by fire)
Heat recovery: Flue gas condensation 2 x 4 MW , Output: 800 kW, Condensation 10 MW, Output: 1,500 kW, Buffer volume: 180 m3
District heating grid: Toblach/Dobbiaco grid built in 1994; Innichen/San Candido grid built in 1999 - Grid length: 90,000 m; pipeline outlet from heating plant DN 200/250, Total connected load (all stations): 20,831 kW (Toblach/Dobbiaco), 21,522 kW (Innichen/San Candido); about 20 additional buildings connected each year
Fuel storage: 80,000 m3 outdoor storage, 5,000 m3 indoor storage
Exhaust gas purification and monitoring: Flue gases are purified of dust using multicyclones, electrical filters and flue gas condensation processes. Combustion emissions are monitored on a continuous basis.
More than 1,000 customers are supplied with renewable energy.